For General Information:
Toll Free: (800) AJPOWER
Local: (813) 996-2583
Fax: (813) 996-5037
nigel at ajpower.com
tad at ajpower.com
MODEL NUMBER CONFIGURATION
AJ’s Power Source Inc. (AJPS) Cage Code (0P327) is pleased to announce the release of our new MIL-CDRSeries. This new series is a Ruggedized Military compliant power conditioning system built for deployment and operations equipment. These units are available to all military, homeland security and government contractors. Built for a Very Low EMI signature and very High Reliability this power system will keep your product up and running for many years to come.
The MIL-CDRSeries is a 1U power conditioning system that provides up to 800 Watts at 115 VAC 60Hz. This is a fully isolated in line double conversion system with input surge protection. This system has many unique features such as over voltage, over current, over temperature and short circuit protection. Stainless steel side rails allow for multiple rack depths and the system has field replaceable filters and fans. This system also contains a 24VDC emergency input that will allow for the system to be powered from any 24VDC source if or when AC inputs are not available.
The conditioner system has been designed to comply with all of the radiated emissions, susceptibility and conductive emissions requirement of the applicable sections of MIL-STD-461E. These techniques have been used successfully by AJPS to comply with these standards many times in the past. The following is a list of methods used for controlling emissions:
Air filters should be placed on a regular maintenance schedule. Suggested inspection should be once a month for any outdoor or high dust environment. The filters can be washed with warm water and soap or blown out in the reverse direction with an air compressor. Regardless of cleaning and inspection processes the filters should be replaced one a year minimum.
The systems rear fans have been design for field replacement and only need replacement in the event of a failure. These fans should be inspected at the same time that the filters are cleaned or changed. If one of the fans is operating slowly, stuttering, or stopped the assembly must be replaced.
OUTPUT POWER CABLES
Output power cables are available upon request. The output power cable will need to be shielded from source to termination if system is required to meet MIL-STD-461E.
|Item||Unit of Measure|
|Input Voltage||VAC||100-264, 47-440Hz|
|Efficiency||%||80 % Typical|
|Hold Up Time||mS||>16 mS at 80% Load|
|Operating Temperature||ºC||–20 to 60ºC|
|Storage Temperature||ºC||-40 to 85ºC|
|Over Voltage Protection||%||130% Standard|
|Short Circuit Protection||%||130% Standard|
|Thermal Protection||Standard||Over Temperature Shut down 70ºC +/- 5ºC|
|Isolation||1500 VDC||Input to Ground and Input to Output|
|Item||Unit of Measure|
|Output Voltage||VAC||115 VAC or 220 VAC|
|Output Power||W||800 Watts|
|Output Frequency||Hz||50Hz +/- .2Hz or 60Hz +/- .2Hz|
|Control and Status||%||SNMP|
|Harmonic Distortion||%||<2% with resistive load|
* Units are designed to meet these standards but, each unit must be tested at system level. Shielded cables and line filters required.